Wireless Gateway for Wall
Lighting Controls-Wireless System
This Wireless Gateway is wall mount type product. The one Gateway is able to configure unto maximum of 127 EA of AG (Access Group) but actually, the AG is configured for 5 EA to operate the Wireless Module.
…International Standard Protocol IEEE 802.15.4 ZIGBEE Communication.
…The maximum of 254 EA Gateway has Stand Alone Function.
…The maximum AG(Access Group) 127 EA
…Actually configured AG is below 5 EA.
…The one Gateway (WG) is configured of less than 5 EA of AG and one AG is designed to have 64 EA of Wireless Dimming Module.
…The Photo adjustment can be set for 254 steps
…16 sets of Scene Setting Functions.
…16 sets of Group Setting Function.
…Individual ON/OFF Control and Individual Dimming Control
…LAMP Status : By the each switch button’s flashing itself, it display the ON/OFF status.
…Connected at ELC communication line and the group and individual control for entire WDM is possible
…The Dimming Control is able to control for each SCENE specific and it has the occupancy detecting and photo detecting sensing function.
…Each Wireless Dimming Module is able to STEP UP and DOWN without Dimming’s FADING.
…The Photo Detecting Sensor and Occupancy Sensor that installed at each Wireless Dimming Module is to choose for operating or no operating due to selection of Enable..
…Each Wireless Dimming Module is internal with Stand Alone Function at CPU, the Dimming Control is able by sensor from site.
…It has Self-Diagnosis function to display the error status for communication error and dimming output error..
…It has the switch function for group, SCENE, DIRECT, INDIRECT function and LOCAL control is possible.
…Performs the broadcasting role between the ELC Network & Wireless Communication.
…Wired and Wireless Communication Integrated Gateway
…Performs the communication between SCU & Smartrol and it is configured for 0 - 255 NODE and the maximum 254 EA of Gateway is configured.
…Stand Alone Function : Schedule, Group Info and Scene Function.
…Remote Control for Individual / Group LED Lighting and Time Schedule Control.
…IEEE 802.15.4 ZIGBEE TO ETHERNET Protocol Conversion
…Operation Power : 12 - 24VDC, 250mA
…Communication : IEEE 802.15.4 ZIGBEE
…Operation Environment : 0 - 40°C, 0 -90% RH
Dimension of Layout
…Applied at Office area
…Applied at Underground Parking Lot area
…Applied at Conference Room
…Applied at Hallway and Lobby area
…Applied at Class room and Restaurant area
…Applied at Office Building, Shopping Mall, Hotel, Residential Complex, Terminal and Public Area to be as efficient management system for Lighting & Black-out.
…Dimming Scene Control for LED Lamp’s Individual & Group.
…The Auto LED Dimming Control due to external Photo.
…The LED Dimming Control due to Movement Detecting Sensor.
…The Installation is easy due to Wireless Communication and the Maintenance is convenient.
…By the Self-Diagnosis Function, the Maintenance is convenient
…The various function is taking advantage due to actual installation of the operating experience.