Wireless ON/OFF & 0-10VDC Module
Full Lighting Controls - Wireless System
The Wireless ON/OFF Module includes the 1EA of 10Ampere Latching Relay and it is consist of International Standard IEEE802.15.4 ZIGBEE communication. Several LED fixtures can be grouped together to turn On/Off wirelessly at once and if necessary, send out the 0-10VDC signal to control the Dimming of LED Fixture.
…International Standard IEEE 802.15.4 ZIGBEE Communication.
…The Max. 254EA of Gateways have Stand Alone Function.
…The Max. 127EA of AG(Access Group).
…Less than 5EA of actual AG configuration.
…The one Gateway(WG) is configured within 5EA of AGs, and one AG is
designed with 64EA Wireless Dimming Modules.
…The LED Fixture Load control up to 10 Ampere circuit.
…100% Dimming by the 0-10VDC Signal.(1 - 254 Steps)
…It has the Self-Diagnosis function to indicate the status of dimming output error & communication error.
…Applied at Office area
…Applied at Underground Parking Lot area
…Applied at Conference Room
…Applied at Hallway and Lobby area
…Applied at Class room and Restaurant area
…Applied at Office Building, Shopping Mall, Hotel,
Residential Complex, Terminal and Public Area to
be as efficient management system for Lighting
…Dimming Scene Control for LED Lamp’s
Individual & Group.
…The Auto LED Dimming Control due to external
…The LED Dimming Control due to Movement
…The Installation is easy due to Wireless
Communication and the Maintenance is
…By the Self-Diagnosis Function, the
Maintenance is convenient
…The various function is taking advantage due to
actual installation of the operating experience.
Dimension of Layout
1.Hardware Function & Structure
…220VAC Power Supply.
…Operating Part : Relay ON/OFF control part, 0~10V
Dimming Control part, Current Sensing part.
…MCU : ZigBee Core Processor.
…Input Power : AC220V, 60Hz
…Operating Power : DC12V, 3.3V, and Other power.
…Operating Part : Relay ON/OFF control,
…Address Setting : 1~64.
…Dimming Control (0~10V) - 1CH Support.
…Latch Relay (16A) - 1EA Internal.
…Operation Source : 220VAC (+-10%), 60Hz.
…Operation Condition : 0 ~ 60°C, 0 ~ 90% RH.
…ZigBee Network : (IEEE 802.15.4).
…The Address of each Wireless Module is set in
order of Gateway > Access Group > WDM.
…The LED FLASH ON/OFF for Warning & Checking
…Self-Diagnosis Function : Communication Error,
Dimming Output Error, Group Info, Scene Info and
Sensor Enable or not)
…Relay ON/OFF Control.
…Group Feeder ON/OFF Control.
…0 ~ 10V Dimming Control (0~100%).
…Address Setting : 1~64.