Lighting Controls-DALI System
The DALI Master is performing the role of converter that interface with the product (DALI Module) for using the DALI Protocol that is connected to ETLC Communication network. From this single DALI Master, connect the DALI Sensor or 64EA of DALI Module, to control the Dimming and several Scene, Pattern, Schedule and ON/OFF by LED Lighting.
…ETLC/DALI Protocol Converting.
…Connect Ballast and 64 EA of DALI Module.
…16 sets of Scene Setting Function.
…16 sets of Group Setting Function.
…Setting for each DALI Module : Group, Scene and Etc.
…DALI Master is able to connect maximum of 999EA at ETLC BUS and single system is able to control the maximum 64,000 EA of DALI Module.
This DALI Master is able to connect up to max. of 999EA at existing lighting control data-line by 001 - 999 address. The each of DALI Master is able to connect up to max. of 64 EA of DALI Module and it is able to control the ON/OFF and Dimming for max. of 64,000 EA of LED Lighting.
The DALI Master is able to operate with existing TLC Network, it can receive the input signal from sensor and switch that connected at TLC Network to control the Preset, Pattern and Dimming. Also the Dimming control by the Photo Sensor and ON/OFF control and Dimming Control by occupancy sensor is possible. The power savings are enhanced greatly.
Also from the central computer, controlling the schedule (Time-Zone), group, pattern is possible by the program. It shows the Dimming Level in percent (%) to suitably used in Lighting Control Management.
…DALI Protocol : IEC 60929
…Baud Rate : 1,200 BPS
…SYSTEM SIZE : 64 units
…CPU : 32Bit Micro Processor
…Mount : Panel Mount Type
…Environment Condition : -10℃ ~ 60℃, 0~95% RH
…Input Power : DC12~24V
…Consume Power : 15W
…Communication Method : TLC NETWORK / DALI
Dimension of Layout