IGS Touch Switch
The IGS Touch Switch is used as Switch and Program Setting Device from RLCM System.
This switch has 4/8 EA switch buttons & 4/8 EA program setting buttons. The LED that displays the Dimming Status in the middle of the switch is indicated by the UP/DN button.
The Dimming Status of the current switch button can be displayed in 10 steps. The Dimming Status can be displayed in 10% increments between 0~100%.
…4/8 switch buttons, 4/8 setting buttons, 10 levels of LED display and Dimming UP/DOWN button.
…Manual Dimming Operation for Individual &Group.
…The Dimming Status is divided into 10 levels and displayed by LED
…Signal Transmission Distance : 500 Meter
…Address Setting : 01~99
…If you have 1EA switch and 1EA Control Module. they can automatically recognized each other for address and settings. Only 1EA of Switch Button is able to control 1EA of Relay
…Use the R(Relay), G(Group), S(Scene) and M(Mixing) buttons of the Program Setup function to set individual group and scene settings for the switches for each control module.
…The part where the corresponding program setting LED display is On is the mode that is operated in the current switch.
This IGS Touch Switch automatically recognizes mutual devices when only one control module is connected. For example, #1 Switch is connected with #1 Relay and #2 Switch is connected with #2 Relay. And if there are several control modules connected to one IGS Touch Switch. set the program by operating the top button of the switch. For example, with 4eRM powered on, the other control module is powered for 5 seconds. Then, #1 and #2 Relay are Grouped and set to the #1 Switch Button for setting with the sounds.
Also, use the Switch while the LED display of the group button is ON.
For setting use the ipper left button when selecting individual relay. For Group. use the upper right button when selecting group relays. For SCENE, use the bottom left button when selecting Dimming Scene. Also when using the Group and SCENE at same time, the bottom right display should be ON.
…Input Power : AC/DC24V(from LCP)
…Operating Condition : -10~60℃, 0~95%
…Current Consumpting : 15mA
…Dimming Status Display : 10EA LED Display.
…Switch Button : 4 / 8 EA
…Program Setting Button : 4 / 8 EA
…Communication Cable & Connector : CAT.6.4pr &RJ45 Jack
…Mounting Size : Standard 1 GANG SWITCH BOX/
…4 Circuits Type - 1 GANG(50X100mm)
…Color : Black & White.
Dimension of Layout
Dimension of Layout