DALI Occupancy Sensor is connected to the same communication lies as existing DALI Module. It is applied as Occupancy Control Sensor for the 64EA of DALI Modules. Occupancy Sensor is applied in the following two types.
.. It is attached to the LDM (DALI Dimming Module) itself and operates as Occupancy Sensor for only one LED Fixture.
.. By the DALI-OCC Sensor, the 64EA of LDMs can be controlled for the Occupancy Control.
-DALI PROTOCOL INTERFACE
-It has the Disable & Enable function and it is applied with schedule control & interlocking control.
-254 steps of Dimming Control Function.
-16 sets of Scene Setting Functions.
-16 sets of Group Setting Functions.
DALI Standard : IEC 62386
-Baud rate : 1,200 BPS
-Data : Individual ON/OFF Control, Individual Dimming Control, Lamp Status/Alarm Signal, Ballast Status/Alarm Signal.
-Dimming range : 5% ~ 100%
-Dimming times : Program
-Do not require a separate shielded communication cables, able to construct with general cable or cable wiring.
-When constructing the cable, able to use the 5C cable (3C-L/N/E, 2C-DALI). Also without installing a separate communication line, construction is possible.
-No need to distinguish between the polarity of communication line.
-Input Voltage : 12~60VDC
-Input Current : 10mA
-IP Rating : 32
-Disable / Enable switching function.
-Default Range : 5M radius
-Operating Temp : 0°C to 55°C
It is installed in meeting room or small office and it may be installed attach of LED fixture and also at separate sensor.
When the single Occupancy Sensor is applied at room, it can detects up to 64EA of LDM (LED DALI DIMMING MODULE) for control.
During Schedule and Interlocking Control, select this occupancy sensor function to Disable to only control the LED by the Schedule Control.